What is Power Usage Effectiveness (PUE) and how is it Calculated?

Posted on October 13, 2014 by Jeanne Ziobro  |  Comment (0)

The Power Usage Effectiveness (PUE) metric which was first introduced by The Green Grid™ in 2007 has become the de facto standard for measuring data center efficiency.  But despite its prevalence, many data center operators are unclear on what PUE is, how it is calculated, and how it can be used to further energy efficiency initiatives. For instance, many data center managers know that their PUE readings should be as close to the number one as possible, but why?

PUE is a ratio of the amount of power needed to operate and cool the data center vs. the amount of power drawn by the IT equipment in the data center.  The equation looks like this:

PUE = (Total Facility Energy) / (IT Equipment Energy)

Thus having a PUE of one would mean that you have a perfect data center where all the power coming into the building makes it to the IT equipment with none used for cooling systems or lighting, or lost in transmission to the IT equipment.

So now that you understand the equation, you may be wondering how you can collect data for both facility and IT equipment.  For facility, most rely on a utility meter.  However, installing what is called a “shadow meter” allows data center operators to track total facility power utilization on a daily basis instead of waiting on the monthly utility bill.

For IT equipment, it is best to collect power data from your rack power distribution units (PDUs) as they can often meter down to the individual outlet level providing insights into the efficiency of individual equipment.  Other times you may be able to collect this information from remote power panels (RPPs) or uninterruptible power supplies (UPS).  And in the event that neither provides metering capabilities, you may consider adding an aftermarket branch circuit meter with split-core current transformers that snaps into existing panels.

The data you collect can be manually added to a worksheet at predetermined intervals and you can set up functions or macros to perform your calculations for you.  Or you can use intelligent rack PDUs that send data over the network to a database that is connected to a DCIM power monitoring solution that will automatically calculate PUE, reveal trends over time, and help data center managers to evaluate how well efficiency initiatives are performing.

Learn more about how Raritan's data center energy management solution automatically calculates PUE or take our DCIM monitoring tool for a spin right from your computer.

Take a Test Drive Now

Other Blog Posts

Are Your Legacy PDUs Putting You at Risk?
Posted on November 16, 2017
Raritan’s Government Data Center and Lab Solutions
Posted on November 8, 2017
Types of Data Center Cooling Techniques
Posted on November 1, 2017
Data Center KPIs to Optimize Capacity Utilization Webinar
Posted on October 25, 2017
Considering Colocation: A Look into Its Advantages, Limitations, and Future Trends
Posted on October 4, 2017

View all Blog Posts

View all Events

Latest Raritan News

Packet, Myriad Supply, Raritan, and Data Center Knowledge to Participate in ‘Managing the Edge’ Webinar
Posted on November 12, 2017
Raritan Employees Support Green Community Projects
Posted on November 8, 2017
Data Center of 2025 — What to Expect
Posted on October 26, 2017
Congratulations to LinkedIn’s Hillsboro, Oregon, Data Center
Posted on July 5, 2017
Raritan Intelligent Infrastructure Solutions Bolster Data Center Performance
Posted on June 26, 2017

View all news